Home / More HVAC parts / Refrigeration Valves / Electronic Expansion Valves / Electronic expansion valve controller Sale!Electronic expansion valve controller Category: Electronic Expansion Valves Description Electronic expansion valve controller,universal version,to control all Electronic expansion valveThe main brands of electronic expansion valves for air conditioners are Sanhua, saginomiya, Danfoss, Emerson, CAREL, DunAn, Fujikoki, etc. This controller can normally drive the above each brand 5-core or 6-core wire, 12 volt, 100-2000 step electronic expansion valve, to achieve automatic adjustment of the opening degree.Place of origin:China , export to worldwide.Order or Inquiry on “ Electronic expansion valve controller” Models & Details for “Electronic expansion valve controller ”The electronic expansion valve controller for air-conditioning has advanced intelligent recognition of cooling and heating modes, intelligent control of cooling and heating superheat, and automatic judgment of the on-off state and defrost state of air-conditioning units. It has nothing to do with the original air-conditioning controller. The main board has integrated power supply, built-in intelligent electronic expansion valve driver, and comes with four-way temperature detection. Specially designed multi-channel protection switching output (exhaust temperature protection, temperature sensor failure protection) can be timely linked with the main controller of the air conditioner, using imported high-speed embedded driver chip, unique automatic half flow and offline function, can protect expansion The valve coil extends the life of the electronic expansion valve. Advanced valve body self-positioning correction technology ensures more accurate control of the electronic expansion valve, preventing misadjustment and overshooting of the electronic expansion valve of the air conditioner. As a result, the air-conditioning unit cannot operate normally! Hairun air-conditioning electronic expansion valve controller can set two working modes: manual mode and automatic mode.The manual mode does not need to install a temperature sensor. It can be used to manually open the valve during air conditioning maintenance. The valve can be closed (evacuated and charged with refrigerant) to determine the failure point of the air conditioning unit and used as a manual valve regulator.In the automatic working mode, the electronic expansion valve of the air conditioner can be independently adjusted. When the electronic expansion valve drive circuit of the original controller of the air-conditioning unit is faulty, the opening degree of the electronic expansion valve can be adjusted independently, so that the air-conditioning unit resumes normal operation.How to purchase “Electronic expansion valve controller ”The item is available for retail and wholesale;The place of origin is in China,when you buy one or two,please consider freight(by air or by sea) into the cost;Accept bulk order with Container delivery;Please contact us to email: email@example.com Product Information Quick Navigation: 1 Electronic expansion valve controller,universal version,to control all Electronic expansion valve 2 Order or Inquiry on “ Electronic expansion valve controller” 2.1 Models & Details for “Electronic expansion valve controller ” 2.2 How to purchase “Electronic expansion valve controller ” 3 Related Products: Related Products:Electronic expansion valve 17C87881A EFM-40YPHS-11R For…Electronic Expansion Valve VPFSanhua Electronic Expansion Valve DPF1.65 1.3C 2.0 1.8C 2.2C…Electronic expansion valve DPF-T / Ts / S series Enquiry or Reviews0/5 Based on 0 rating(s) 5 Star 0 % 0 review(s)4 Star 0 % 0 review(s)3 Star 0 % 0 review(s)2 Star 0 % 0 review(s)1 Star 0 % 0 review(s)0 Star 100 % 1 review(s) Reviewed by 01 customer(s) Veijo Rantanen Hi, is this card compatible with pressure transmitter? -How can I connect it? – Is there a guide for this?Best regards Veijo Rantanen Hartola Finland 2021-08-08 Reply Write enquiry message or review Cancel reply Rate Your Satisfaction*
Hi, is this card compatible with pressure transmitter?
-How can I connect it?
– Is there a guide for this?