Digital Thermostat module Model XH-W1316,two relay output
Item: Digital Thermostat module Model XH-W1316,two relay output
Specifications Model: XH-W1316
Temperature control: on-off
Control mode: heating, cooling;
Temperature control range: -50℃-110 ℃
Control accuracy: +/- 0.1 ℃
Power supply voltage: DC12V/24v,AC220V
Output: Relay output,two channels
Appearance size: 82 * 58*30mm
Place of origin: China factory sell directly , Sell to worldwide.
|Order or Inquiry on “Digital Thermostat module Model XH-W1316”|
|Models & Details for “Digital Thermostat module Model XH-W1316”|
he controller is the type of Relay outputting,output contacting tip means a switcher,so,need to connect the tip into the power-supply circuit.
How to use?
1,set stop temperature: press SET a time,flashing a number on the screen,set this number as stop temperature,at what temperature you want to stop,then set this number as stop temperature.
2,set working mode: press SET key long time,after 5seconds,showing F1 on screen;then,press SET key again,set to be “H” or “C”.
3,Set Return value: when showing F1 on the screen,press ” ” a time,when showing F2 on the screen,press SET key again,set the value of F2.
The mode of Speeding up:
the controller has two channels output(Output1 and output2).No need divide for two channels.For example,when set Return value “5”,when the difference between real temperature and stop temperature is bigger than 5,then will start the second output,and thus start the mode of Speeding Up.
The use of heating mode:
Refer to the way 1.2.3 above,set temperature difference(enter F3 to set temperature difference).
F1: working mode
H: indicates that work in the heating mode; C: indicates cooling mode
F2: Hysteresis setting(Return value setting)
Hysteresis = controlling maximum temperature -controlling minimium temperature, Example: control between 35-40,
Then the hysteresis is 5 (40-35 = 5 so the hysteresis is set to 5)
F3: Temperature difference setting
Can set a group of temperature difference, when the first red lighter bright,when the difference between the real-time temperature and stop temperature is greater than the F3 set value, then the second red lighter bright, start the two devices.
When the difference between the real-time temperature and the stop temperature is less than the set value of F3, the second red light does not bright, the second channel relay has no output.
F4: Set the upper temperature limit (no need to set)
F5: Set the lower temperature limit (no need to set)
F6: Temperature calibration
When there is errer between the display temperature and the actual temperature , can be corrected through this function, after correction,the value will be automatically added to the real-time temperature, the current display temperature = the last display temperature + calibration value.
F7: high temperature alarm
When the temperature is higher than the set value, the LED flashes
Notice: You need to connect heating device or cooling device on both Output 1 and Output 2. Couldn`t one channel connect heating device,and the other conntect cooling device.
|Buying Guide to “Digital Thermostat module Model XH-W1316”|
- The Digital Thermostat Module Model XH-W1316 is available for retail and wholesale;
- Accept customized bulk production,putting your logo;
- The place of origin is in China,when you buy one or a small quantity,please consider freight into the cost;
- Accept bulk order with Container delivery;
- Please contact us to email: [email protected] or [email protected] ,we can supply a favourite item you need.