Models and Details for “Digital Thermostat Module Model XH-W1209 temperature controller ”
Thermostat Range: -50℃ to 110℃
Thermostat Accuracy: 0.1℃
Power Supply: DC12V
Output: 1 output Max 10A relay.
12V / red light /with 1meter probe
1,100% complete machine chip, wave soldering, stable performance, good consistency;
2, embedded central processor chip (MCU), better intelligent, lower power consumption;
3, power-off settings automatically memory (MCU built-in EEPROM storage unit)
4, the control accuracy of 0.1 ℃;
5, hysteresis 0.1 from the set, you can control the decimal (0.1-15.0)
Thermostat range: -50 ~ 110 ℃;
Resolution: 0.1 ℃ between -9.9 ~ 99.9 ℃; 1℃ at other range;
Temperature measurement accuracy: 0.1 ℃;
Control accuracy: 0.1 ℃;
Backlash accuracy: 0.1 ℃;
Refresh rate: 0.5 S;
High Temperature Alarm: 0 ~ 110 ℃;
Motherboard Power Supply: DC 12V;
Output: 1 channel relay output, capacity=10A;
Measurement input: NTC (10K 0.5%) Waterproof sensor;
Environmental requirements: -10 ℃ ~ 60 ℃, Humidity 20% -85%;
Size: 48 * 40mm;
Power consumption: Quiescent Current: ≤35MA;Attract current≤65MA;
How to operate:
After wire ,then can supply power to the device, display ambient temperature.Press SET key a time,screen flash the temperature.press key of + – to set the desired temperature. (long-time to press key of + – to get a quick setting). after set the temperature,press SET to confirm and return, then the controller automatically do power- on or power-off Relay.The thermostat output 10A relay to meet a variety of high-power load, please sure to connect the correct circuit.
Indicator light, digital tube and buzzer status
Indicator light: Flashing indicates the cooling or heating delay-start . If the indicator is on, it indicates that the relay is closed
Digital tube: display “LL” means sensor is connected; display “HH” means over the measuring range,then the thermostat is force to disconnect the relay; display “—‘ means high temperature alarm.
Long-time press SET ket 5 seconds,then enter main setting menu,press + – key to change P0 to P8.Long-time press SET key or no any press 10seconds,automatically confirm and return.
|Code||Indicating||Set range||Inital Setting|
|P0||Mode set(Heating or Cooling)||C/H||C|
|P1||Set return difference||0.1-15||2|
|P5||Delay start time||0-10 minutes||0|
|At “OFF” state, Long press + -,start and then recovery to inital set|
- The Digital Thermostat Module Model XH-W1209 is available for retail and wholesale;
- Accept customized bulk production,putting your logo;
- The place of origin is in China,when you buy one or a small quantity,please consider freight into the cost;
- Accept bulk order with Container delivery;
- Please contact us to email: email@example.com or firstname.lastname@example.org ,we can supply a favourite item you need.