Condensate Removal Pump
Condensate Removal Pump Type A
Condensate Removal Pump Type B
Condensate Removal Pump is used for remove condensate water in inlaid type,ceiling suspended and disconnect-type air conditioners.
This type Condensate Removal Pump is a total system,for remove condensate water in inlaid type,ceiling suspended and disconnect-type air conditioners,which can`t be removed naturally.Its design has two parts: pump room/control equipment,water storage tank add on automatic switch. These two parts can be installed in air conditioners,or pump room/control equipment can be installed on ceiling ,which above the water storage tank within 1 meter.Floating control of water storage tank is seperated into three parts:start-up,cease and safety warming switch.Enclose: inlet pipe,clamp,cloth insertion sheet,exhaust pipe and drain pipe.
Condensate Removal Pump`s characteric:
1),Full rotation type;start up,cease,water-line spilled over safety warming switch(start-up warmer or turn off air conditioner.
2),Designed as two parts,used for easilly and quickly install.
3),Pump is auto-suction type,can be installed in air conditioner,or place in it above tank within 1 meter.
4),Water storage tank connects on13-17 mm wash port in air conditioner.
5),Max. flow: 14k/h(3.7US gallon).
7),Operating range:6kl/h while head is 4m(1.6US Gallon/h while head is 13.1feet)
8),Used for air conditioner equipment,max is 10KW(30000BTU)(4KW used in wet areas).
9),Exhaust pipe enclose water storage tank.
10),Overheating auto poweroff protective device.
11),Design of pump exit used for 4x6mm(5/32 inch diameter of water pipe).
13)eNCLOSE:sELF-ABSORPTION WATER PIPE:1MX4MM(31/4 FEET X 5/32 inch inner diameter).Exhaust pipe:150MMX4MM(6INCHX5/32inch inner diameter) Drain pipe of air conditioner:75mmx13mm(3inchx1/2inch inner diamter)
How to removal the condensates from the air conditioning?
Condensates (drops of water caused by warm, humid air passing over a
cold surface) are formed In sir conditioning, refrigeration and condensing
boiler units. There are 2 ways of removing them;
1. Evacuate the condensates by gravity, which means dealing with
technical and aesthetic problems (distant drainage outlet, not enough
fall, damage to walls and unsightly pipe work)
2. Instal a condensate removal pump (smaller dimensions. the appearance
of the installation is preserved for pearl spring series, simple and quick
to install for clear spring series, safer as equipped with alarm and non
What is a Condensate Removal Pump?
It is a system condensates gravity fall which consists
to be evacuated of a pump unit and a detection unit allowing
to a water drainage outlet where there is no gravity fall.
This technology has 3 advantages:
1. It protects the appearance of the customer’s Installation (nounsightly pipework) 2. Easy, simple and safe to install
3. Reduction of the risk of bacterial contamination by waste water (no stagnation or back-flow of water due to non return valves)