Air to air heat exchanger Recuperator
This air to air heat exchanger recuperator keep indoor air fresh, exchange heat between indoor and outdoor air.
Air to air heat exchanger recuperator,keep indoor air fresh,capture energy from the drain-out air,220V,50HZ
Air to air heat exchanger ,also names recuperator,air energy exchanger.It is a compact enclosure device which is used in the field of ventilation for air freshing and heat exchanging. In the building with this device installed,you can get fresh air immediately,and at the same time,it can recovery heat energy from the drain out air,save your electricity consumption. Best air filtering result,low noise and excellent energy recovery performance.
- Air volume(Standard type): 150m³/h,200m³/h,250m³/h,350m³/h,500m³/h,600m³/h,800m³/h, 1000m³/h,1200m³/h,1500m³/h,2000m³/h
- Air volume (Commerical type): 3000m³/h,4000m³/h, 5000m³/h, 6000m³/h, 8000m³/h, 10000m³/h, etc…For more volume,accept customize.
- Heat recovery percentage: 72.83%;
- Air filtering performance: 99%
- Noise: from 26db(A) to 63db(A) depends on different model;
- Connecting pipe diameter: φ150mm,φ200mm,φ250mm,depends on different model;
- For size and more details, please check below table.
Place of origin: Made in China factory, export to worldwide.
Models of Standard type:
Model of Commerical type:
How to install “Air to air heat exchanger Recuperator”?
How to purchase Air to air heat exchanger Recuperator ?
- The item is available for retail and wholesale;
- The place of origin is in China,when you buy one or two,please consider freight(by air or by sea) into the cost;Suggest delivery by sea ship.
- Accept bulk order with Container delivery;
- Please contact us to email: [email protected]
General knowledge for Air Recuperator
Working princip of recuperator:
The working principle of the full heat exchanger is: when the product is working, indoor air is exhausted and outer fresh air flowing through the core of the heat exchanger in a crosswise manner, due to the temperature difference and steam partial pressure difference between the air flows on both sides of the air separation plate, the two air flows show heat and mass transfer phenomenon when passing through the separation plate, causing a total heat exchange process. . During summer operation, the fresh air obtains cooling capacity from the air conditioning exhaust air to reduce the temperature, and at the same time is dried by the air conditioning air to reduce the moisture content of the fresh air. During winter operation, the fresh air receives heat from the air conditioning room exhaust air and the temperature increases. In this way, through the full heat exchange process of the heat exchange core, fresh air is recovered from the air conditioning exhaust air.
do not smoke
Fresh air volume required per person (m / h)
Room fresh air ventilation times P (times / h)
Q1 = n · q = 12 × 50 = 600 (m³ / h).
If calculated according to the number of fresh air exchanges in the room, take the number of fresh air ventilations in the room p = 4.5 (times / h).
Then the fresh air flow Q2 = p · s · h = 4.5 × 50 × 3 = 675 (m³ / h).
Since Q2> Q1, Q2 (ie 675m³ / h) is taken as the data of the equipment selection parameter.