Digital Thermostat Module Model XH-W1308
Item: Digital Thermostat Module Model XH-W1308
Description: Digital Thermostat Module
Thermostat Range: -55℃ to 120℃
Thermostat Accuracy: 0.1℃
Screen Color: Blue or Red
Power Supply: 5V/12V/24V, 220V;
Output: Max 10A
Temperature Probe Wire: 0.5meter,anti-water;
Whole Size: 100x48x28mm
Flush/embed Size: 71x41mm
Hole Distance: M3/86mm
Place of origin: China factory sell directly , Sell to worldwide.
|Order or Inquiry on “Digital Thermostat Module Model XH-W1308”|
|Models & Details for “Digital Thermostat Module Model XH-W1308 ”|
12V / red light / with panel and 1meter probe
|Code||Indicating||Set range||Inital Setting|
|P1||Return Difference Setting||0.1-30||2.0|
|P4||Temp. adjust||+10 to -10||0|
|P5||Delay Time Start||0-10 minutes||0|
|Operation on “Digital Thermostat Module Model XH-W1308”|
How to set temperature?
When you switch on,the real temperature will be displayed; Push “SET” one time,the screen flash,and then push
arrow(up or down) to set temperature;
How to enter more SETTING?
Long Pushing “SET”(5s)to enter more setting;And push “ENT” to confirm and return last menu;In the normal working,Long pushing can lead to Switching Off;
When you are first time to use this digital thermostat module,you must set to be “PO”;If works for heating,set to be “H”;If
working for cooling,set to be “G”;
P1: temperature range value
For example: set Heating mode,temperature 37℃-40℃,then the value is 3.
P2-P3:to set temperature range for thermostat
P4:Adjust temperature error
This function is to adjust temperature error.If there has some error between real temperature and tested temperature,you can
use this function. The adjusted value=tested value + adjusted value. For example,we tested temperature 25.6℃,but real
temperature is 25.8℃,then you can set P4 to be 0.2,then the final temperature is 25.6℃+0.2=25.8℃;
This function is used for compressor refrigerating.If you want this device to use on the refrigerator,then this value must be
set.Accoring to compressor returning pressure,generally set 3-6minutes;If you don`t to control compressor,or don`t need
delaying function,please skip this set.
P6:Alarm for high temperature
When the real temperature is over than the set value,the screen will show “HHH” and the buzzer will alarm sound “di di di”,at
the same time,will cut off output to protect electric circuit.
P7:Value lock.To prevent other people to modify the setting.After you set all values,you can enter “P7”,and set to be
“On”,then,all values couldn`t be modified,unless enter “P7” again to set to be “Off”;
P8:Recovery all value to be inital state.
|Buying Guide to “Digital Thermostat Module Model XH-W1308”|
- The Digital Thermostat Module Model XH-W1308 is available for retail and wholesale;
- Accept customized bulk production,putting your logo;
- The place of origin is in China,when you buy one or a small quantity,please consider freight into the cost;
- Accept bulk order with Container delivery;
- Please contact us to email: firstname.lastname@example.org or email@example.com ,we can supply a favourite item you need.